The 61C614 model is a passive termination panel that was made by Reliance Electric for the AutoMate series. This device, however, is no longer manufactured by the OEM but can still typically be found in AX Control’s stock.
The 61C614 termination panel is designed to be used with the 61C613 analog input module. The purpose of the 61C614 termination panel is to terminate voltage and thermocouple inputs from the 61C13 module. In addition to that, the 61C614 termination panel can also terminate current inputs by connecting a resistor across the terminal strip. If you are in need of the 61C613 analog input module to go along with your 61C614 termination panel, then you can click on the link in the first sentence of this paragraph to be taken to its dedicated page on our website. From there, you can learn more about it and find out if it is available in our stock.
The 61C614 termination panel includes two 50-wire flat cables that are both six feet long. This device also includes 32 clamp-type barrier strips that are used for terminating field signals. These barrier strips are screw-activated.
The 61C614 termination panel’s installation process is quite simple. First, be sure that the whole system’s power is turned off. Then, mount the termination panel in such a way that there is easy access to the terminal board’s terminal board and that the terminal board is close to the rack so that its cable can reach both the terminal board and the module. After the panel is mounted, you can fasten the field wires to the terminal strip. Next, connect the 50-pin flat cables directly to the 61C614 termination panel and their connector on the 61C613 analog input module. When all of these steps are completed, you can turn the power on to the system and begin operation.