The GE Power Excitation Board DS200RTBAG3AGC is an optional board that is installed in the drive cabinet and it features ten relays that are driven either directly from the pilot relays or remotely by the user. The DS200RTBAG3AGC board contains jumpers, RPL connectors, OPTPL connectors, stab connectors, C1PL and Y9PL connectors, and terminal points that you can use to configure the board.
The board contains 15 jumpers that enable you to control some aspects of the behavior of the board. For example, you can configure the board to use an external or internal power source for the relay coils. You can also configure the board to use power from the CPH to power the pluggable Y31PL circuit. The factory settings are provided on a data sheet so you can easily return the board to the original factory configuration.
To change a jumper setting you must make sure the board contains no current. You must disconnect the drive from power and wait a few seconds for all power to leave the board. The board has components that store current during normal operation. Then, test the board with a testing device to verify that no current exists in the board.
Locate the jumper you want to change and use your fingers to lift the jumper off one set of pins and insert the jumper over the other set of pins. For example, move the jumper from pins 1 and 2 and insert the jumper over pins 2 and 3. Do not touch other components on the board and do not lose or drop the jumper.