When using the F4-04DAS-2 Isolated Output Module with the H4-EBC Ethernet Base Controller, make sure the H4-EBC contains firmware version 2.1.46 or later.
32 discrete output points in the CPU are required by the F4–04DAS–2 Analog Output Module. The module can be installed in any slot of a DL405 system, including remote bases.
The available power budget and I/O points are limitations you must consider when you determine the number of modules.
The F4-04DAS-2 Isolated Output Module is a 4 channel output module. The output voltages are in the range between 0 to 5VDC and 0 to 10VDC. The number of channels is 4 (isolated). The resolution is 16 bit (1 in 65536). Allow for 60mA at 5VDC (supplied by base) when you plan the power allocation. When you consider the operational environment, know that corrosive gases are not permitted.
Between 1 channel and 4 channels can be scanned for the PLC update rate.
The output points required is 16 data bits, 2 channel ID, 1 output enable 32 (Y) output points.
The F4-04DAS-2 Isolated Output Module contains valuable hardware features.
The analog outputs are isolated from other outputs.
You can easily remove the terminal block.
All analog outputs may be set in one CPU scan, only if a DL440 CPU or a DL450 CPU is being used.
Loop power supplies allow you to have four channels of isolated current outputs.